In order to complete the power supply for the diesel generator set , in addition to the unit itself, the power distribution system, parallel system and related control accessories are required to work normally and reliably. All links are more important, otherwise they may fail. Unable to complete emergency power supply.
For example, the parallel operation of diesel generator sets requires the cooperation of related control cables, relays, and contactors. In a humid environment, the relays and contactors may appear rusted and adhered, and may fail during real use, or even control line connections. Looseness and fall-off may cause failure to achieve parallel operation.
Therefore, daily inspections should pay attention to check whether the related accessories of the diesel generator set work normally, whether the knob is in the correct position, pay attention to every detail, and find out the hidden dangers and deal with it in time. The monthly test machine also directly adopts the parallel test machine in order to find out in time whether there is a problem with the related accessories of the parallel system.
To do a good job of maintenance of diesel generator sets, the maintenance personnel should patiently and meticulously perform routine maintenance and testing in accordance with the requirements of maintenance procedures. They must be sufficiently sensitive to the hidden problems found during the operation and maintenance process, and deal with and eliminate them as soon as possible. Hidden dangers, at the same time, thoroughly analyze the cause of the failure, find out the real cause, and focus on summing up the experience of troubleshooting to avoid similar failures from happening again. Only in this way can we guarantee the emergency power supply of the diesel generator set at any time, and ensure the safe and reliable power supply of the communication network equipment.